SPEC 80211

## 35kV AL 100% TRXLPE Two-Thirds Neutral (Based on Short Circuit) HI-DRI-PLUS® Renewable (Solar or Wind)

#### Moisture Blocked Aluminum Conductors. TRXLP Insulation. Two-Thirds Copper Concentric Neutral. XLPE Jacket

#### Construction:

- Conductor:Moisture Blocked 1350 H16/H26 Aluminum, Class B Compressed or Compressed Unilay Stranded
- Strand Shield:Semi-conducting Crosslinked Polyethylene
- Insulation:Tree Retardant Crosslinked Polyethylene (TRXLP)
- Insulation Shield:Strippable Semi-conducting Crosslinked Polyethylene
- Concentric Neutral:Annealed Copper Wires Helically Applied Two-Thirds Concentric Neutral
- Overall Jacket & Water Block:HI-DRI-PLUS® Water Swellable Powder Black Crosslinked Polyethylene (XLPE) with Red Extruded Stripes

#### Applications and Features:

- Predominately used for renewable projects with wind or solar applications.
- Suitable for use in wet or dry locations, direct burial, underground ducts, and exposure to direct sunlight.
- To be used at conductor temperature not to exceed 105ºC normal operation.
- UL listed MV-105
- The concentric neutral counts and sizes listed in Table 1 are based on the ICEA P-45-482 short circuit calculation of an MV-90 design. The short circuit value in Table 1 is calculated using a higher thermal limit of a crosslinked XLPE jacket MV-105 design.

#### Specifications:

#### Sample Print Legend:

{SQFTG} SOUTHWIRE(R) HI-DRI-PLUS(R) (UL) XXX AWG AL 345 MILS TRXLPE TYPE MV-105 35KV 100% INSUL LEVEL -- (NESC) -- SOUTHWIRE {MMM} {YYYY} NON-CONDUCTING JACKET

Table 1 – Weights and Measurements

Stock Number | Cond. Size | Diameter Over Conductor | Diameter Over Insulation | Insul. Thickness | Diameter Over Insulation Shield | Concentric Neutral | Neutral DC Resistance 25°C | Jacket Thickness | Approx. OD | Approx. Weight | Min Bending Radius | Max Pull Tension |
---|---|---|---|---|---|---|---|---|---|---|---|---|

AWG/Kcmil | inch | inch | mil | inch | No. x AWG | Ω/1000ft | mil | inch | lb/1000ft | inch | lb | |

626288^{} | 1/0 (19) | 0.361 | 1.072 | 345 | 1.182 | 8x14 | 0.328 | 50 | 1.410 | 808 | 11.3 | 633 |

TBA^{} | 2/0 (19) | 0.395 | 1.123 | 345 | 1.233 | 10x14 | 0.263 | 50 | 1.461 | 952 | 11.7 | 798 |

TBA^{} | 3/0 (19) | 0.443 | 1.171 | 345 | 1.281 | 12x14 | 0.219 | 50 | 1.509 | 1049 | 12.1 | 1006 |

TBA^{} | 4/0 (19) | 0.498 | 1.226 | 345 | 1.336 | 15x14 | 0.175 | 50 | 1.564 | 1172 | 12.5 | 1269 |

TBA^{} | 250 (37) | 0.558 | 1.294 | 345 | 1.404 | 18x14 | 0.146 | 75 | 1.682 | 1386 | 13.5 | 1500 |

TBA^{} | 350 (37) | 0.661 | 1.397 | 345 | 1.507 | 26x14 | 0.101 | 75 | 1.785 | 1674 | 14.3 | 2100 |

TBA^{} | 500 (37) | 0.789 | 1.525 | 345 | 1.665 | 23x12 | 0.046 | 75 | 1.977 | 2365 | 15.8 | 3000 |

All dimensions are nominal and subject to normal manufacturing tolerances

◊ Cable marked with this symbol is a standard stock item

* Pulling tension based on pulling eye directly connected to conductor

Table 2 – Electrical and Engineering Data

Cond. Size | DC Resistance @ 25°C | AC Resistance @ 90°C | Capacitive Reactance @ 60Hz | Inductive Reactance @ 60Hz | Charging Current | Dielectric Loss | Zero Sequence Impedance | Positive Sequence Impedance | Short Circuit Current @ 30 Cycle | Allowable Ampacity in Duct 90°C | Allowable Ampacity Directly Buried 90°C |
---|---|---|---|---|---|---|---|---|---|---|---|

AWG/Kcmil | Ω/1000ft | Ω/1000ft | MΩ*1000ft | Ω/1000ft | A/1000ft | W/1000ft | Ω/1000ft | Ω/1000ft | Amp | Amp | Amp |

1/0 (19) | 0.167 | 0.211 | 0.071 | 0.053 | 0.28 | 1.71 | 0.265 + j0.747 | 0.211 + j0.054 | 4138 | 160 | 195 |

2/0 (19) | 0.133 | 0.167 | 0.067 | 0.052 | 0.30 | 1.80 | 0.221 + j0.744 | 0.167 + j0.051 | 5173 | 185 | 220 |

3/0 (19) | 0.105 | 0.132 | 0.063 | 0.050 | 0.32 | 1.93 | 0.186 + j0.740 | 0.132 + j0.050 | 6207 | 210 | 250 |

4/0 (19) | 0.084 | 0.105 | 0.058 | 0.048 | 0.34 | 2.08 | 0.159 + j0.735 | 0.105 + j0.048 | 7759 | 235 | 280 |

250 (37) | 0.071 | 0.090 | 0.054 | 0.047 | 0.37 | 2.24 | 0.144 + j0.730 | 0.090 + j0.047 | 9311 | ||

350 (37) | 0.050 | 0.065 | 0.048 | 0.045 | 0.42 | 2.52 | 0.119 + j0.723 | 0.065 + j0.045 | 13449 | 315 | 370 |

500 (37) | 0.035 | 0.046 | 0.042 | 0.043 | 0.47 | 2.86 | 0.100 + j0.714 | 0.046 + j0.043 | 29588 | 380 | 435 |

*****Ampacities for Direct Buried are based on ICEA P-117-734-2016 Single-Conductor Solid Dielectric 15-35kV. Single Circuit Flat Direct Buried Figure 3

*****Ampacities for Duct are based on ICEA P-117-734-2016 for Single-Conductor Solid Dielectric 15-35kV. Single Circuit Trefoil Conduit Figure 7.

*****Sequence Impedance values are based on Rho Earth Resistivity: 100 Ohm-Meter/1000ft.

Table 3 – Weights and Measurements (Metric)

Stock Number | Cond. Size | Diameter Over Conductor | Diameter Over Insulation | Insul. Thickness | Diameter Over Insulation Shield | Concentric Neutral | Neutral DC Resistance 25°C | Jacket Thickness | Approx. OD | Approx. Weight | Min Bending Radius | Max Pull Tension |
---|---|---|---|---|---|---|---|---|---|---|---|---|

AWG/Kcmil | mm | mm | mm | mm | No. x AWG | Ω/km | mm | mm | kg/km | mm | newton | |

626288^{} | 1/0 (19) | 9.17 | 27.23 | 8.76 | 30.02 | 8x14 | 1.08 | 1.27 | 35.81 | 1202 | 287.02 | 2817 |

TBA^{} | 2/0 (19) | 10.03 | 28.52 | 8.76 | 31.32 | 10x14 | 0.86 | 1.27 | 37.11 | 1417 | 297.18 | 3551 |

TBA^{} | 3/0 (19) | 11.25 | 29.74 | 8.76 | 32.54 | 12x14 | 0.72 | 1.27 | 38.33 | 1561 | 307.34 | 4477 |

TBA^{} | 4/0 (19) | 12.65 | 31.14 | 8.76 | 33.93 | 15x14 | 0.57 | 1.27 | 39.73 | 1744 | 317.50 | 5647 |

TBA^{} | 250 (37) | 14.17 | 32.87 | 8.76 | 35.66 | 18x14 | 0.48 | 1.91 | 42.72 | 2063 | 342.90 | 6675 |

TBA^{} | 350 (37) | 16.79 | 35.48 | 8.76 | 38.28 | 26x14 | 0.33 | 1.91 | 45.34 | 2491 | 363.22 | 9345 |

TBA^{} | 500 (37) | 20.04 | 38.73 | 8.76 | 42.29 | 23x12 | 0.15 | 1.91 | 50.22 | 3520 | 401.32 | 13350 |

All dimensions are nominal and subject to normal manufacturing tolerances

◊ Cable marked with this symbol is a standard stock item

* Pulling tension based on pulling eye directly connected to conductor

Table 4 – Electrical and Engineering Data (Metric)

Cond. Size | DC Resistance @ 25°C | AC Resistance @ 90°C | Capacitive Reactance @ 60Hz | Inductive Reactance @ 60Hz | Charging Current | Dielectric Loss | Zero Sequence Impedance* | Positive Sequence Impedance* | Short Circuit Current @ 30 Cycle | Allowable Ampacity in Duct 90°C | Allowable Ampacity Directly Buried 90°C |
---|---|---|---|---|---|---|---|---|---|---|---|

AWG/Kcmil | Ω/km | Ω/km | MΩ*km | Ω/km | A/km | W/km | Ω/1000ft | Ω/1000ft | Amp | Amp | Amp |

1/0 (19) | 0.5479 | 0.69 | 0.0216 | 0.1739 | 0.919 | 5.6102 | 0.265 + j0.747 | 0.211 + j0.054 | 4138 | 160 | 195 |

2/0 (19) | 0.4364 | 0.55 | 0.0204 | 0.1706 | 0.984 | 5.9055 | 0.221 + j0.744 | 0.167 + j0.051 | 5173 | 185 | 220 |

3/0 (19) | 0.3445 | 0.43 | 0.0192 | 0.1640 | 1.050 | 6.3320 | 0.186 + j0.740 | 0.132 + j0.050 | 6207 | 210 | 250 |

4/0 (19) | 0.2756 | 0.34 | 0.0177 | 0.1575 | 1.115 | 6.8241 | 0.159 + j0.735 | 0.105 + j0.048 | 7759 | 235 | 280 |

250 (37) | 0.2329 | 0.30 | 0.0165 | 0.1542 | 1.214 | 7.3491 | 0.144 + j0.730 | 0.090 + j0.047 | 9311 | ||

350 (37) | 0.1640 | 0.21 | 0.0146 | 0.1476 | 1.378 | 8.2677 | 0.119 + j0.723 | 0.065 + j0.045 | 13449 | 315 | 370 |

500 (37) | 0.1148 | 0.15 | 0.0128 | 0.1411 | 1.542 | 9.3832 | 0.100 + j0.714 | 0.046 + j0.043 | 29588 | 380 | 435 |

*****Ampacities for Direct Buried are based on ICEA P-117-734-2016 Single-Conductor Solid Dielectric 15-35kV. Single Circuit Flat Direct Buried Figure 3

*****Ampacities for Duct are based on ICEA P-117-734-2016 for Single-Conductor Solid Dielectric 15-35kV. Single Circuit Trefoil Conduit Figure 7.

*****Sequence Impedance values are based on Rho Earth Resistivity: 100 Ohm-Meter/1000ft.

Revision: 1.000.011

Updated On: Jan. 18, 2024, 10:06 p.m. UTC

Concentric Neutral Calculator