MC-PCS HCF Duo™ Power & Control/Signal Cable 277/480V
Copper THHN/THWN Insulated Singles. Green Insulated Copper Grounding Conductor. UL Listed 600 Volts. Rated VW-1. Lightweight Interlocked Armor. Signal: 16 AWG Copper TFN insulated singles.
- Conductor:Solid copper per ASTM B3 and ASTM B8
- Insulation:All phases are insulated with Polyvinyl Chloride with Nylon Sheath Type THHN/THWN
- Ground:Green insulated ground. Polyvinyl Chloride with Nylon Sheath Type THHN/THWN
- Signal:16 AWG Copper TFN Insulated Singles Pink, Purple. Overall light blue jacket over the signal cables
- Binder:Mylar tape
- Ground:Full-sized bare 8000 series aluminum grounding/bonding conductor. Armor and bare aluminum conductor form the equipment ground path.
- Armor:Lightweight Interlocked Armor
Applications and Features:
Southwire MC-AP HCF Type MC All Purpose Hospital Care Facility Cable is suitable for use as follows:Branch-circuit wiring for patient care areas of hospitals, medical centers, and other health care facilities (when installed in accordance with NEC® Articles 517 and 330, and mechanically protected per Article 300.4). Such areas include nursing homes, dental offices, clinics, and outpatient facilities. Use in hazardous anesthetizing areas is prohibited.Applications requiring redundant, dedicated or isolated grounding paths.Fished or embedded in plaster.Concealed or exposed installations.Environmental air-handling spaces per NEC 300.22 (C).Places of Assembly per NEC 518.4 and theaters per NEC 520.5.Power, lighting, control, and signal circuits.Installation in cable tray and approved raceways.Under raised floors for information technology equipment conductors and cables per NEC 645.5(D) & 645.5(D)(2)Class I Div. 2, Class II Div 2, & Class III Div. 1 Hazardous Locations.Use with UL Listed MCI-A fittings.Binder tape with print legend wrapped around assembly.Type THHN/THWN rated 90ºC Dry.
Southwire Armorlite® Type MC Cable - meets or exceeds the following requirements:
UL Online Product Guide Info - Metal-Clad Cable (PJAZ) ( www.ul.com )Federal Specification A-A59544 (formerly J-C-30B)NFPA 70 (National Electrical Code), Article 330Listed for use in UL 1, 2 and 3 Hour Through Penetration Firestop Systems
Specifications:ASTM B3 Soft or Annealed Copper WireASTM B8 Concentric-Lay-Stranded Copper ConductorsUL 83 Thermoplastic Insulated Wires and CablesUL 1569 Metal-Clad CablesUL 1479 Standard for Safety Fire Tests of Penetration FirestopsUL 1685 FT4 Vertical-Tray Fire Propagation and Smoke Release TestIEEE 1202 FT4 Flame Test (70,000) BTU/hr Vertical Tray TestBuy American: Compliant with Buy American Requirements, found in 49 U.S.C. § 5323(j); specify “Made in the USA Only!” when ordering to ensure your project receives American made products.REACH - European Community Regulation
Sample Print Legend:
ALUMINUM CLAD CABLE WITH COPPER CDRS TYPE THHN OR THWN MAX VOLTAGE 600V, FOR USE IN CABLE TRAY90(D)C - WET OR DRY LOCATIONS GASOLINE & OIL RESISTANT CDRS LISTED FOR FIREWALL PENTRATION (GREEN INSULATED GROUND)
Table 1 – Weights and Measurements
Table 2 – Electrical and Engineering Data
Updated On: Aug. 21, 2023, 12:19 p.m. UTC