"Table 1 - Weights and Measurements"
""
"Stock Number","Cond. Size","Conductor Number","Conductor Stranding","Diameter Over Conductor","Insul. Thickness","Diameter Over Insulation","Diameter Over Insulation Shield","Ground","Jacket Thickness","Approx. OD","Approx. Weight","Max Pull Tension","Min Bending Radius"
"","AWG/Kcmil","","","inches","mils","inches","inches","No. x AWG","mils","inches","lbs./MFT","lbs.","inches"
"956490","2","3","7","0.282","220","0.755","0.815","1x6","110",2.032,"2236","1592","14.2"
"958306","1/0","3","19","0.361","220","0.840","0.900","1x4","110",2.215,"2758","2534","15.5"
"558254","2/0","3","19","0.405","220","0.884","0.944","1x4","110",2.310,"3237","3194","16.1"
TBA,"3/0","3","19","0.456","220","0.934","0.994","1x3","110",2.422,"3504","4027","16.9"
"956284","4/0","3","19","0.512","220","0.976","1.036","1x3","110",2.516,"4288","5078","17.6"
TBA,"4/0","3","19","0.512","220","0.990","1.050","1x3","110",2.543,"4044","5078","17.8"
"558288","250","3","37","0.558","220","1.028","1.088","1x2","110",2.628,"4815","6000","18.3"
"671989","350","3","37","0.661","220","1.147","1.207","1x1/0","135",2.935,"6288","8400","20.5"
"958322","350","3","37","0.661","220","1.147","1.207","1x2","135",2.935,"6213","8400","20.5"
"958330","500","3","37","0.789","220","1.252","1.312","1x1","135",3.162,"7973","12000","22.1"
"578614","500","3","37","0.789","220","1.275","1.335","1x4/0","135",3.203,"8374","12000","22.4"
TBA,"500","3","37","0.789","220","1.275","1.335","1x1","135",3.208,"7706","12000","22.4"
"653562","750","3","61","0.968","220","1.464","1.524","1x1/0","135",3.620,"11048","18000","25.3"
"558312","750","3","61","0.968","220","1.464","1.524","1x1/0","135",3.620,"11040","18000","25.3"
"All dimensions are nomial and subject to normal manufacturing tolerances"
"Table 2 - Electrical and Engineering Data"
"Cond. Size","DC Resistance @ 25C","AC Resistance @ 90C","Capacitive Reactance","Inductive Reactance","Zero Sequence Impedance","Positive Sequence Impedance","Shield Short Circuit Current 6 Cycles","Allowable Ampacity In Duct 90/105C","Allowable Ampacity In Air 90/105C"
"AWG/Kcmil","ohm/MFT","ohm/MFT","Mohm*MFT","Mohm/MFT","ohm/MFT","ohm/MFT","Amps","Amps","Amps"
"2","0.162","0.204","0.051","0.047","0.579 + j0.421","0.204 + j0.048","2571","150/160","165/185"
"1/0","0.102","0.128","0.043","0.043","0.5 + j0.385","0.128 + j0.043","2816","195/210","215/240"
"2/0","0.081","0.102","0.040","0.042","0.471 + j0.367","0.102 + j0.042","2952","220/235","245/275"
"3/0","0.064","0.081","0.037","0.040","0.447 + j0.347","0.081 + j0.04","3110","250/270","285/315"
"4/0","0.051","0.065","0.034","0.039","0.426 + j0.328","0.065 + j0.039","3284","285/305","325/360"
"4/0","0.051","0.065","0.034","0.039","0.426 + j0.328","0.065 + j0.039","3284","285/305","325/360"
"250","0.043","0.056","0.032","0.038","0.413 + j0.31","0.056 + j0.038","3451","310/335","360/400"
"350","0.031","0.041","0.028","0.036","0.388 + j0.28","0.041 + j0.036","3770","375/400","435/490"
"350","0.031","0.041","0.028","0.036","0.388 + j0.28","0.041 + j0.036","3770","375/400","435/490"
"500","0.022","0.030","0.025","0.034","0.365 + j0.248","0.03 + j0.034","4167","450/485","535/600"
"500","0.022","0.030","0.025","0.034","0.365 + j0.248","0.03 + j0.034","4167","450/485","535/600"
"500","0.022","0.030","0.025","0.034","0.365 + j0.248","0.03 + j0.034","4167","450/485","535/600"
"750","0.014","0.023","0.021","0.032","0.339 + j0.21","0.024 + j0.032","4752","545/585","670/745"
"750","0.014","0.023","0.021","0.032","0.339 + j0.21","0.024 + j0.032","4752","545/585","670/745"