"Table 1 - Weights and Measurements"
""
"Stock Number","Cond. Size","Conductor Number","Conductor Stranding","Diameter Over Conductor","Insul. Thickness","Diameter Over Insulation","Diameter Over Insulation Shield","Jacket Thickness","Approx. OD","Approx. Weight","Max Pull Tension","Min Bending Radius"
"","AWG/Kcmil","","","inches","mils","inches","inches","mils","inches","lbs./MFT","lbs.","inches"
TBA,"2","1","Solid","0.257","175","0.645","0.725","80",0.985,"446","398","11.8"
TBA,"2","1","7","0.282","175","0.670","0.750","80",1.010,"461","398","12.1"
TBA,"1","1","Solid","0.289","175","0.677","0.757","80",1.017,"482","502","12.2"
TBA,"1","1","19","0.322","175","0.710","0.790","80",1.050,"500","502","12.6"
TBA,"1/0","1","Solid","0.324","175","0.712","0.792","80",1.052,"523","633","12.6"
TBA,"1/0","1","19","0.351","175","0.739","0.819","80",1.079,"540","633","12.9"
TBA,"2/0","1","19","0.395","175","0.783","0.863","80",1.123,"592","798","13.5"
TBA,"3/0","1","19","0.443","175","0.831","0.911","80",1.171,"654","1006","14.1"
TBA,"4/0","1","19","0.498","175","0.886","0.966","80",1.226,"728","1269","14.7"
TBA,"250","1","37","0.558","175","0.954","1.034","80",1.294,"808","1500","15.5"
TBA,"350","1","37","0.661","175","1.057","1.137","80",1.397,"964","2100","16.8"
TBA,"500","1","37","0.789","175","1.185","1.265","80",1.525,"1181","3000","18.3"
TBA,"750","1","61","0.968","175","1.374","1.454","110",1.774,"1656","4500","21.3"
TBA,"1000","1","61","1.117","175","1.523","1.603","110",1.923,"1994","6000","23.1"
"All dimensions are nomial and subject to normal manufacturing tolerances"
"Table 2 - Electrical and Engineering Data"
"Cond. Size","DC Resistance @ 25C","AC Resistance @ 90C","Charging Current","Dielectric Loss","Capacitive Reactance","Inductive Reactance","Zero Sequence Impedance","Positive Sequence Impedance","Shield Short Circuit Current 6 Cycles","Allowable Ampacity Directly Buried 90/105C","Allowable Ampacity In Duct 90/105C","Allowable Ampacity In Air 90/105C"
"AWG/Kcmil","ohm/MFT","ohm/MFT","Amp/1000ft","watt/1000ft","Mohm*MFT","Mohm/MFT","ohm/MFT","ohm/MFT","Amps","Amps","Amps","Amps"
"2","0.162","0.204","0.212","15.8","0.040","0.053","0.551 + j0.267","0.205 + j0.053","2064","150/","120/","/"
"2","0.266","0.336","0.225","16.8","0.038","0.051","0.678 + j0.256","0.337 + j0.051","2133","150/","120/","/"
"1","0.129","0.162","0.228","17.0","0.037","0.051","0.503 + j0.253","0.163 + j0.051","2153","170/","140/","/"
"1","0.211","0.266","0.244","18.2","0.035","0.049","0.601 + j0.239","0.267 + j0.049","2244","170/","140/","/"
"1/0","0.102","0.128","0.246","18.3","0.035","0.049","0.462 + j0.238","0.129 + j0.049","2250","195/","155/","/"
"1/0","0.167","0.211","0.259","19.3","0.033","0.047","0.540 + j0.228","0.212 + j0.048","2325","195/","155/","/"
"2/0","0.133","0.167","0.280","20.9","0.030","0.046","0.488 + j0.213","0.168 + j0.046","2446","220/","180/","/"
"3/0","0.105","0.132","0.303","22.6","0.028","0.044","0.444 + j0.198","0.133 + j0.045","2580","250/","200/","/"
"4/0","0.084","0.105","0.330","24.6","0.026","0.042","0.407 + j0.183","0.106 + j0.043","2732","285/","235/","/"
"250","0.071","0.090","0.363","27.0","0.023","0.041","0.381 + j0.166","0.091 + j0.042","2920","335/","256/","/"
"350","0.050","0.065","0.412","30.7","0.020","0.039","0.339 + j0.145","0.066 + j0.039","3206","375/","310/","/"
"500","0.035","0.046","0.474","35.3","0.018","0.037","0.301 + j0.125","0.047 + j0.037","3561","450/","375/","/"
"750","0.024","0.033","0.564","42.0","0.015","0.036","0.263 + j0.102","0.035 + j0.036","4084","550/","470/","/"
"1000","0.018","0.026","0.635","47.3","0.013","0.034","0.240 + j0.088","0.028 + j0.035","4497","630/","/"