"Table 1 - Weights and Measurements"
""
"Stock Number","Cond. Size","Diameter Over Conductor","Diameter Over Insulation","Diameter Over Insulation Shield","Ground","Jacket Thickness","Approx. OD","Approx. Weight","Max Pull Tension","Min Bending Radius"
"","AWG/Kcmil","inches","inches","inches","No. x AWG","mils","inches","lbs./MFT","lbs.","inches"
"669083","4/0","0.512","0.766","0.826","3 x 6","110",2.267,"4067","5078","15.8"
"669084","350","0.661","0.917","0.977","3 x 6","110",2.593,"5653","8400","18.1"
"669087","500","0.789","1.042","1.102","3 x 5","110",2.913,"7552","12000","20.3"
"669090","750","0.968","1.254","1.314","3 x 4","135",3.371,"10509","18000","23.5"
"All dimensions are nomial and subject to normal manufacturing tolerances"
"Table 2 - Electrical and Engineering Data"
"Cond. Size","DC Resistance @ 25C","AC Resistance @ 90C","Capacitive Reactance","Inductive Reactance","Zero Sequence Impedance","Positive Sequence Impedance","Shield Short Circuit Current 6 Cycles","Allowable Ampacity In Duct 90/105C","Allowable Ampacity In Air 90/105C"
"AWG/Kcmil","ohm/MFT","ohm/MFT","Mohm*MFT","Mohm/MFT","ohm/MFT","ohm/MFT","Amps","Amps","Amps"
"4/0","0.051","0.065","0.0233","0.0335","0.437 + j0.429","0.065 + j0.034","2409","265/280","285/320"
"350","0.031","0.041","0.0196","0.0315","0.409 + j0.367","0.041 + j0.032","2859","355/380","395/440"
"500","0.022","0.03","0.0171","0.0302","0.39 + j0.325","0.03 + j0.03","3227","430/460","485/545"
"750","0.014","0.023","0.015","0.029","0.368 + j0.274","0.023 + j0.029","3769","530/570","615/685"